text:
Steam-electric power station
From Wikipedia, the free encyclopedia
Jump to: navigation, search
This article is an orphan, as no other articles link to it. Please introduce links to this page from related articles; try the Find link tool for suggestions. (December 2012)
This article needs additional citations for verification. Please help improve this article by adding citations to reliable sources. Unsourced material may be challenged and removed. (November 2015) (Learn how and when to remove this template message)
Mohave Generating Station, a 1,580 MW steam-electric power plant near Laughlin, Nevada fuelled by coal
A steam-electric power station is a power station in which the electric generator is steam driven. Water is heated, turns into steam and spins a steam turbine which drives an electrical generator. After it passes through the turbine, the steam is condensed in a condenser. The greatest variation in the design of steam-electric power plants is due to the different fuel sources.
Almost all coal, nuclear, geothermal, solar thermal electric power plants, waste incineration plants as well as many natural gas power plants are steam-electric. Natural gas is frequently combusted in gas turbines as well as boilers. The waste heat from a gas turbine can be used to raise steam, in a combined cycle plant that improves overall efficiency.
Worldwide, most electric power is produced by steam-electric power plants, which produce about 86% of all electric generation[citation needed]. The only other types of plants that currently have a significant contribution are hydroelectric and gas turbine plants, which can burn natural gas or diesel. Photovoltaic panels, wind turbines and binary cycle geothermal plants are also non-steam electric, but currently do not produce much electricity.
Contents
[hide]
1 History
2 Efficiency
3 Steam plant
3.1 Condenser
3.2 Feedwater heater
3.3 Boiler
3.4 Superheater
4 See also
5 References
6 External links
History[edit]
Reciprocating steam engines have been used for mechanical power sources since the 18th Century, with notable improvements being made by James Watt. The very first commercial central electrical generating stations in New York and London, in 1882, also used reciprocating steam engines. As generator sizes increased, eventually turbines took over due to higher efficiency and lower cost of construction. By the 1920s any central station larger than a few thousand kilowatts would use a turbine prime mover.
Efficiency[edit]
The electric efficiency of a conventional steam-electric power plant, considered as saleable energy produced at the plant busbars compared with the heating value of the fuel consumed, is typically 33 to 48% efficient, limited as all heat engines are by the laws of thermodynamics (See: Carnot cycle). The rest of the energy must leave the plant in the form of heat. This waste heat can be disposed of with cooling water or in cooling towers. If the waste heat is instead utilized for e.g. district heating, it is called cogeneration. An important class of steam power plants are associated with desalination facilities; these are typically found in desert countries with large supplies of natural gas and in these plants, freshwater production and electricity are equally important co-products.
Since the efficiency of the plant is fundamentally limited by the ratio of the absolute temperatures of the steam at turbine input and output, efficiency improvements require use of higher temperature, and therefore higher pressure, steam. Historically, other working fluids such as mercury have been experimentally used in a mercury vapour turbine power plant, since these can attain higher temperatures than water at lower working pressures. However, the obvious hazards of toxicity, and poor heat transfer properties, have ruled out mercury as a working fluid.
Steam plant[edit]
Condenser[edit]
Main article: Surface condenser
Diagram of a typical water-cooled surface condenser
Steam-electric power plants utilize a surface condenser cooled by water circulating through tubes. The steam which was used to turn the turbine is exhausted into the condenser. The steam is therefore condensed as it comes in contact with the cool tubes full of circulating water. This condensed steam is withdrawn from the bottom of the surface condenser. The condensed steam is now water, commonly referred to as condensate water.
The adjacent image is a diagram of one of the many typical surface condenser designs.[1][2][3][4]
For best efficiency, the temperature in the condenser must be kept as low as practical in order to achieve the lowest possible pressure in the condensing steam. Since the condenser temperature can almost always be kept significantly below 100 oC where the vapor pressure of water is much less than atmospheric pressure, the condenser generally works under vacuum. Thus leaks of non-condensable air into the closed loop must be prevented. Plants operating in hot climates may have to reduce output if their source of condenser cooling water becomes warmer; unfortunately this usually coincides with periods of high electrical demand for air conditioning. If a good source of cooling water is not available, cooling towers may be used to reject waste heat to the atmosphere. A large river or lake can also be used as a heat sink for cooling the condensers; temperature rises in naturally occurring waters may have undesirable ecological effects, but may also incidentally improve yields of fish in some circumstances.[citation needed]
Feedwater heater[edit]
Main article: Feedwater heater
A Rankine cycle with a two-stage steam turbine and a single feedwater heater.
In the case of a conventional steam-electric power plant utilizing a drum boiler, the surface condenser removes the latent heat of vaporization from the steam as it changes states from vapor to liquid. The heat content (btu) in the steam is referred to as Enthalpy. The condensate pump then pumps the condensate water through a feedwater heater. The feedwater heating equipment then raises the temperature of the water by utilizing extraction steam from various stages of the turbine.[1][2]
Preheating the feedwater reduces the irreversibilities involved in steam generation and therefore improves the thermodynamic efficiency of the system.[5] This reduces plant operating costs and also helps to avoid thermal shock to the boiler metal when the feedwater is introduced back into the steam cycle.
Boiler[edit]
Once this water is again inside the boiler or steam generator, the process of adding the latent heat of vaporization or Enthalpy is underway. The boiler transfers energy to the water by the chemical reaction of burning some type of fuel. The water enters the boiler through a section in the convection pass called the economizer. From the economizer it passes to the steam drum. Once the water enters the steam drum it goes down the downcomers to the lower inlet waterwall headers. From the inlet headers the water rises through the waterwalls and is eventually turned into steam due to the heat being generated by the burners located on the front and rear waterwalls (typically). As the water is turned into steam/vapor in the waterwalls, the steam/vapor once again enters the steam drum. The steam/vapor is passed through a series of steam and water separators and then dryers inside the steam drum. The steam separators and dryers remove the water droplets from the steam and the cycle through the waterwalls is repeated. This process is known as natural circulation.
Any droplets of liquid water carried over into the turbine can produce destructive erosion of the turbine blades.
Geothermal power station in Iceland
Geothermal plants need no boiler since they use naturally occurring steam sources. Heat exchangers may be used where the geothermal steam is very corrosive or contains excessive suspended solids. Nuclear plants also boil water to raise steam, either directly passing the working steam through the reactor or else using an intermediate heat exchanger.
Superheater[edit]
As the steam is conditioned by the drying equipment inside the drum, it is piped from the upper drum area into an elaborate set up of tubing in different areas of the boiler. The areas known as superheater and reheater. The steam vapor picks up energy and its temperature is now superheated above the saturation temperature. The superheated steam is then piped through the main steam lines to the valves of the high-pressure turbine.
See also[edit]
Boiler
Combined heat and power
Cooling tower system
Flue gas stacks
Fossil fuel power plant
Geothermal power
Nuclear power plant
Power station
Thermal power station
Water-tube boiler
References[edit]
^ Jump up to: a b Babcock & Wilcox Co. (2005). Steam: Its Generation and Use (41st ed.). ISBN 0-9634570-0-4.
^ Jump up to: a b Thomas C. Elliott, Kao Chen, Robert Swanekamp (coauthors) (1997). Standard Handbook of Powerplant Engineering (2nd ed.). McGraw-Hill Professional. ISBN 0-07-019435-1. CS1 maint: Multiple names: authors list (link)
Jump up ^ Air Pollution Control Orientation Course from website of the Air Pollution Training Institute
Jump up ^ Energy savings in steam systems Figure 3a, Layout of surface condenser (scroll to page 11 of 34 pdf pages)
Jump up ^ Fundamentals of Steam Power by Kenneth Weston, University of Tulsa
External links[edit]
Power plant diagram
Power Plant Reference Books
[[es:Central termoel�ctrica]] [[gl:Central t�rmica]] [[pt:Central termoel�trica]]
Retrieved from "https://en.wikipedia.org/w/index.php?title=Steam-electric_power_station&oldid=815126788"
Categories:
Power station technology
Chemical process engineering
Energy conversion
Hidden categories:
CS1 maint: Multiple names: authors list
Orphaned articles from December 2012
All orphaned articles
Articles needing additional references from November 2015
All articles needing additional references
All articles with unsourced statements
Articles with unsourced statements from August 2007
Articles with unsourced statements from March 2015
Pages using div col with deprecated parameters
Navigation menu
Personal tools
Not logged in
Talk
Contributions
Create account
Log in
Namespaces
Article
Talk
Variants
Views
Read
Edit
View history
More
Search
Navigation
Main page
Contents
Featured content
Current events
Random article
Donate to Wikipedia
Wikipedia store
Interaction
Help
About Wikipedia
Community portal
Recent changes
Contact page
Tools
What links here
Related changes
Upload file
Special pages
Permanent link
Page information
Wikidata item
Cite this page
Print/export
Create a book
Download as PDF
Printable version
Languages
العربية
Български
Deutsch
Edit links
This page was last edited on 12 December 2017, at 22:34.
Text is available under the Creative Commons Attribution-ShareAlike License; additional terms may apply. By using this site, you agree to the Terms of Use and Privacy Policy. Wikipedia® is a registered trademark of the Wikimedia Foundation, Inc., a non-profit organization.
Privacy policy
About Wikipedia
Disclaimers
Contact Wikipedia
Developers
Cookie statement
Mobile view
Enable previews

values: mw-page-base noprint

values: mw-head-base noprint

values: firstHeading firstHeading en

values: siteSub noprint

values: jump-to-nav mw-jump

attrs: rel class href

value: tbody

values: plainlinks metadata ambox ambox-style ambox-Orphan

values: Help:Introduction to referencing with Wiki Markup/1

values: plainlinks metadata ambox ambox-content ambox-Refimprove

attrs: alt src width height class srcset data-file-width data-file-height

values:
/wiki/Fossil_fuel_power_plant
mw-redirect
Fossil fuel power plant

values:
/wiki/Solar_thermal_electric
mw-redirect
Solar thermal electric

values: Flue gas emissions from fossil fuel combustion

values: This claim needs references to reliable sources. (August 2007)

values:
noprint Inline-Template Template-Fact
white-space:nowrap;

values:
/wiki/Photovoltaic_panel
mw-redirect
Photovoltaic panel

values:
/wiki/Cooling_water
mw-redirect
Cooling water

attrs: alt src width height class data-file-width data-file-height

values: This claim needs references to reliable sources. (March 2015)

values:
/wiki/Drum_boiler
mw-redirect
Drum boiler

values:
/wiki/Latent_heat_of_vaporization
mw-redirect
Latent heat of vaporization

values:
/wiki/Thermodynamic_efficiency
mw-redirect
Thermodynamic efficiency

values:
/wiki/Combined_heat_and_power
mw-redirect
Combined heat and power

values:
/wiki/Cooling_tower_system
mw-redirect
Cooling tower system

values:
/wiki/Flue_gas_stacks
mw-redirect
Flue gas stacks

values: div-col columns column-count column-count-2

values: -moz-column-count: 2; -webkit-column-count: 2; column-count: 2;

values: Category:CS1 maint: Multiple names: authors list

values:
reflist mw-references-wrap
list-style-type: decimal;

values:
nofollow
external text
http://www.tva.gov/power/coalart.htm

values: Category:Orphaned articles from December 2012

values: Category:Articles needing additional references from November 2015

values: Category:All articles needing additional references

values: Category:All articles with unsourced statements

values: Category:Articles with unsourced statements from August 2007

values: Category:Articles with unsourced statements from March 2015

values: Category:Pages using div col with deprecated parameters

values: Discussion about edits from this IP address [ctrl-alt-n]

values:
/wiki/Steam-electric_power_station
View the content page [ctrl-alt-c]
c

values:
/wiki/Main_Page
Visit the main page [ctrl-alt-z]
z

values: Featured content – the best of Wikipedia

values: Find background information on current events

values:
/wiki/Special:Random
Load a random article [ctrl-alt-x]
x

values: A list of recent changes in the wiki [ctrl-alt-r]

values: List of all English Wikipedia pages containing links to this page [ctrl-alt-j]

values: Recent changes in pages linked from this page [ctrl-alt-k]

values:
/wiki/Wikipedia:File_Upload_Wizard
Upload files [ctrl-alt-u]
u

values: A list of all special pages [ctrl-alt-q]

values: Permanent link to this revision of the page

values: Link to connected data repository item [ctrl-alt-g]

values: Printable version of this page [ctrl-alt-p]

values:
uls-settings-trigger
Language settings
0
button
true

values: محطة توليد بخارية – Arabic

values: Топлоелектрическа централа – Bulgarian

values: /static/images/wikimedia-button-1.5x.png 1.5x, /static/images/wikimedia-button-2x.png 2x

values: /static/images/poweredby_mediawiki_132x47.png 1.5x, /static/images/poweredby_mediawiki_176x62.png 2x

values:
suggestions
display: none; font-size: 13px;

values: mediawiki ltr sitedir-ltr mw-hide-empty-elt ns-0 ns-subject page-Steam-electric_power_station rootpage-Steam-electric_power_station skin-vector action-view